Electrical Installations test and inspected the earth leakage. We found the earth leakage to be faulty and had to replace it. Electrical Installations also found on the earth leakage plug tester that the polarities of live and neutral was reversed, and we rectify it.
We also removed old Geyser timer and fixed flickering light switch.
For all your tripping problems call us Alwyn on 064 247 3812